Service: HVAC Commissioning and Water Treatment
Project: Alder Hey Children’s Hospital
Client: Crown House Technologies & Laing O’Rourke
The new state-of-the-art Alder Hey Children’s Hospital is the first of its kind. This £237m facility boasts a low carbon footprint and low energy use, with 60% of energy needed to run Alder Hey in the Park being generated on-site. Cleartech Group Ltd were awarded the HVAC commissioning and water treatment works for this project. Working in partnership with Crown House Technologies and Laing O’Rourke, we formed an integral part of the project team, ensuring successful delivery of the project on time and on budget. We are particularly delighted to be a part of such a fantastic project.
Scope of Works:
Pre-commission clean of heating and chilled systems in accordance with BSRIA BG29/2012. Systems included:
- LTHW primary – 60,000 litres
- LTHW secondary serving zone 1 to 7 – 65,000 litres
- CHW serving zone 1 to 7- 72,000 litres
- GSHP cooling – 5,400 litres
- GSHP heating (inc UFH) – 10,000 litres
- Heat rejection circuits – 15,840
Disinfection of domestic water system. Systems include:
- Internal and external pipework
- 6 CWSTs
- 2 rainwater tanks
Pre Commission Cleaning
Cleartech’s team of highly experienced HVAC commissioning and water treatment engineers carried out the pre-commission clean of all heating and chilled systems using side stream technology. This included the set up of hoses, chemicals, IBCs and the flushing & filling rig, in a safe and controlled area, as well as filling and flushing all systems in accordance with BSRIA BG29/2012. All heating and chilled systems were sampled and tested on a weekly basis to ensure chemical dosage rates were correct and compliant. All side streams were monitored daily with filter bags being cleaned/changed where required, ensuring a continuous efficient cleaning process.
All heating and chilled systems (inc LTHW CT and LTHW VT) systems were balanced on a zone by zone basis in line with current CIBSE codes. Cleartech also balanced the domestic water (systems), and set up and tested all TMV’s (thermostatic mixing valves) including fail-safes.
Domestic Water System Disinfection
Cleartech disinfected all domestic water systems. On completion of disinfection works in each section/zone, sentinel outlets were sampled to ensure TVC’s, E.coli, Coliforms and Pseudomonas were of an acceptable level to allow handover.
You can learn more about the hospital by clicking this link.
For further information or advice on HVAC commissioning and water treatment, or for a quote, call today on 01355 267199, send an email to email@example.com or submit a contact form on our website.
Click the graphic to view or download the Alder Hey Children’s Hospital case study.